Now let us come back to the concept of the notification proxy-model and configure our regulator so it can be used by supervisors (while still being a supervisor to its own servants).
We will build this:
The below illustration shows what you will build in this tutorial. The red dots indicate tutorial steps.
While you component has a built-in supervisor (marked in green on the drawing below), you need to establish an interface to it so that the component will display the functionality you have designed to its supervisor.
This interface is established via a proxy record.
The proxy record must contain the following elements:
It is possible to rename the record elements, but remember to document such changes carefully, so other programmers can use your component.
Actual should be defined as a record and its first element must be of data type PD_7883 - Condition_def. This is used to communicate the condition of the component.
Actual can contain e.g. component state or component value
The data type of Required and the extra fields in Actual can be adapted to the application.
Step 1: create supervisor data.
We will now modify our temperature regulator component, so that it receives a set point from the supervisor (i.e. "Required" holds the set point) and turns Output on if the actual temperature is lower than set point. We (still) want the regulation mechanism to run whenever the actual temperature has changed (ie. Actual.Actual_temperature contains the temperature read from the servant Temperature) or the set point has changed
Open your control component XX_Temperature_Regulator_Notification
Note that we have renamed Required to "Set_Point".
Assign the variable to the Supervisor in your temperature control component.
Note that Set_point and Actual_rec.Actual_temperature are of type [Absolute temperature].
Step 2: Adjusting the regulating algorithm
Our regulation must run when
- the actual temperature (measured by the servant component "Temperature" changes, i.e. the same mechanism that we implemented in a previous tutorial.
- the set point changes. The set point will be provided by the supervisor via the register "Required" and the method "Required_changed".
We already implemented the first element (in calculate actual of the control component):
You need to read the new setpoint (ie. Required) into the local variable and then run the regulation (ie call method calculate actual).
Your code in "Required_changed" should look like this:
Calculating the condition
The condition of a component is calculated from the error state of the component and the condition of its servants.
The condition of an lower level servant is automatically rippling up to higher level supervisors.
Step 3: calculating the condition
Our temperature regulator has two servants i.e. temperature and output. For this tutorial we will assume that the control component itself cannot generate any errors, so the condition of the control component is calculated from the conditions of the two servants.
Open your control component "XX-Temperature_regulator_notification" Open method "Calculate actual".
Write your code so that the condition of the component is the larger of the two servant conditions.
code to add:
We already handled step 1 (the regulation algorithm). This step can be elaborated much more to take into account errors, control mode and servant information. But we will leave that for a later tutorial.
We also handled step 2 (assumed no errors) and step 3 (calculate the condition).
So all we need to do to finalise the format is step 4 where we update the Actual record (which inform the supervisor of the new data).
Step 4: Updating the Actual record.
Our Actual record contain two records: Condition and Actual_temperature.
We already sent the condition (via the SetCondition method) so all we need to do is update Actual. And recall that this value needs to be the actual temperature as read by the servant "Temperature".
Code to add:
Your total code in "calculate actual" needs to look something like this:
Having completed the changes to the component, we now need to make the updates to the visualisation.
Step 5: Update your visualisation.
Right click on view list - add - view for control instance - find the supervisor of XX-temperature_regulator_notification- actual rec- condition, double click and select "PD_15375 - Show_Condition_without_auto_state". Set "Disable hit test". This will avoid the opening of the default window for this data type.
Launch the graphical editor and drag the condition visualisation to a suitable position.
Your visualisation should look something like this:
We have now prepared our temperature regulator component to be controlled by a supervisor, but it can (of course) still run on its own. And now the component can display its condition (that we calculated in step 3), so let us explore this before moving on.
Step 6: Save, build and run your project.
Open your project ""XX_Temperature_Regulator_notification_project". Save, build project, start project downloader (make sure your test bed is still connected and that the PC device is started) and config all modules.